;------------------------------------------------------------------------------
; This GSD (General Station Description) is provided by PI C3PG7 "PA Profile".
; This GSD is available for download at PI web server.
; The Profile GSDs cover the common subset of functions of devices of
; a specific PA device type providing interchangeability.
;
; This file describes the device type:
; Flow Transmitter - Ultrasonic
; with 2 Analog Inputs and 1 Totalizer
; Physical layer MBP.
; This file becomes valid with the PA profile version 4.0.
;
; Last modification: 2017-10-20
;------------------------------------------------------------------------------
#Profibus_DP
;Standard definitions, valid for all device types with MBP
GSD_Revision = 5
Vendor_Name = "Profile Process Control Devices"
Revision = "PA 4.x"
Protocol_Ident = 0
Station_Type = 0
FMS_supp = 0
Hardware_Release = "-"
Software_Release = "-"
31.25_supp = 1
45.45_supp = 1
93.75_supp = 1
187.5_supp = 1 ;needed to support spec. network devices
500_supp = 1 ;needed to support spec. network devices
1.5M_supp = 1 ;needed to support spec. network devices
3M_supp = 1 ;needed to support spec. network devices
6M_supp = 1 ;needed to support spec. network devices
12M_supp = 1 ;needed to support spec. network devices
MaxTsdr_31.25 = 100
MaxTsdr_45.45 = 250 ;exception for spec. network devices
MaxTsdr_93.75 = 1000
MaxTsdr_187.5 = 60
MaxTsdr_500 = 100
MaxTsdr_1.5M = 150
MaxTsdr_3M = 250
MaxTsdr_6M = 450
MaxTsdr_12M = 800
Redundancy = 0
Repeater_Ctrl_Sig = 0
24V_Pins = 0
Freeze_Mode_supp = 0
Sync_Mode_supp = 0
Set_Slave_Add_supp = 1
Min_Slave_Intervall = 250
Modular_Station = 1
Slave_Family = 12@Profile4
;end of standard definitions
;Device type specific definitions
Model_Name = "Ultrasonic flow (PhyL 1)"
Ident_Number = 0xB334
Bitmap_Device = "PA_B334n"
Max_Module = 3
Max_Input_Len = 15 ;2*AI(2*5) + 1*TOT(5)
Max_Output_Len = 1 ;SET_TOT
Max_Data_Len = 16
Max_Diag_Data_Len = 31
Modul_Offset = 1
Max_User_Prm_Data_Len = 29
Ext_User_Prm_Data_Const(0) = 0x80 ;DPV1 Status 1
Ext_User_Prm_Data_Const(1) = 0x00 ;DPV1 Status 2
Ext_User_Prm_Data_Const(2) = 0x08 ;DPV1 Status 3
;--- Startup parameter of the Physical Block (Slot 0)
PrmText = 1 ;STARTUP_PARAM_VALIDITY
Text(0) = "Ignored"
Text(1) = "Applied"
EndPrmText
ExtUserPrmData = 1 "Startup parameters"
Unsigned8 0 0-1
Prm_Text_Ref = 1
EndExtUserPrmData
Ext_User_Prm_Data_Const(3) = 5,66,0,0,0x00
Ext_User_Prm_Data_Ref(7) = 1 ;STARTUP_PARAM_VALIDITY (Unsigned8)
;--- Startup parameter of the transducer block - Ultrasonic flow (Slot 1)
PrmText = 2 ;volume flow units
Text(1349) = "m3/h"
Text(1351) = "L/s"
Text(1357) = "ft3/min"
Text(1363) = "gal/min"
EndPrmText
ExtUserPrmData = 2 "Unit (Volume flow)"
Unsigned16 1349 0-65535
Prm_Text_Ref = 2
EndExtUserPrmData
PrmText = 3 ;sound velocity
Text(1061) = "m/s"
Text(1067) = "ft/s"
EndPrmText
ExtUserPrmData = 3 "Unit (sound velocity)"
Unsigned16 1061 0-65535
Prm_Text_Ref = 3
EndExtUserPrmData
Ext_User_Prm_Data_Const(8) = 8,68,1,0,0x05,0x45,0x04,0x25
Ext_User_Prm_Data_Ref(12) = 2 ;volume flow unit (Unsigned16)
Ext_User_Prm_Data_Ref(14) = 3 ;sound velocity unit (Unsigned16)
;--- Startup parameters of the Volume Totalizer (Slot 3)
PrmText = 4
Text(1034) = "m3"
Text(1038) = "L"
Text(1043) = "ft3"
Text(1048) = "gal"
EndPrmText
ExtUserPrmData = 4 "Unit (Volume)"
Unsigned16 1034 0-65535
Prm_Text_Ref = 4
EndExtUserPrmData
Prm_Block_Structure_supp = 1
PrmCmd_supp = 1 ;slave supports PrmCmd
Slave_Max_Switch_Over_Time = 20 ;=200 ms
Slave_Redundancy_supp = 1 ;slave is not redundant but can be connected to a flying master
Info_Text = "Ultrasonic flow transmitter with PROFIBUS PA (MBP) \
communication interface."
Ident_Maintenance_supp = 1
;----------- Description of extended DP features: ---------------------
;
DPV1_Slave = 1
C1_Read_Write_supp = 1
C1_Max_Data_Len = 128
C1_Response_Timeout = 400
C2_Read_Write_supp = 1
C2_Max_Data_Len = 128
C2_Max_Count_Channels = 1
Max_Initiate_PDU_Length = 52
C2_Response_Timeout = 400
DPV1_Data_Types = 0
WD_Base_1ms_supp = 0
Check_Cfg_Mode = 0
;----------- Description of device related diagnosis: ---------------------
;
Unit_Diag_Bit(16) = "Status appears"
Unit_Diag_Bit(17) = "Status disappears"
Unit_Diag_Bit(35) = "Restart" ;DIA_WARMSTART
Unit_Diag_Bit(36) = "Application reset" ;DIA_COLDSTART
Unit_Diag_Bit(37) = "Maintenance required" ;DIA_MAINTENANCE
Unit_Diag_Bit(40) = "Maintenance alarm" ;DIA_MAINTENANCE_ALARM
Unit_Diag_Bit(41) = "Maintenance demanded" ;DIA_MAINTENANCE_DEMANDED
Unit_Diag_Bit(42) = "Function check" ;DIA_FUNCTION_CHECK
Unit_Diag_Bit(43) = "Out of specification" ;DIA_OUT_OF_SPEC
Unit_Diag_Bit(44) = "Parameter update" ;DIA_UPDATE_EVENT
Unit_Diag_Bit(55) = "Extension available"
;NE107_COMMON
Unit_Diag_Bit(56) = "Sensor element exciter faulty"
Unit_Diag_Bit_Help(56) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(57) = "Error in evaluation electronics"
Unit_Diag_Bit_Help(57) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(58) = "Error in internal energy supply"
Unit_Diag_Bit_Help(58) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(59) = "Error in sensor element"
Unit_Diag_Bit_Help(59) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(60) = "Error in actuator element"
Unit_Diag_Bit_Help(60) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(61) = "Faulty installat e.g. dead space"
Unit_Diag_Bit_Help(61) = "Check installation."
Unit_Diag_Bit(62) = "Parameter setting error"
Unit_Diag_Bit_Help(62) = "Check parameter settings for consistency."
Unit_Diag_Bit(63) = "Signal path broken or short cut"
Unit_Diag_Bit_Help(63) = "Check signal path."
Unit_Diag_Bit(64) = "Overloading"
Unit_Diag_Bit_Help(64) = "Check load."
Unit_Diag_Bit(65) = "Wrong polarity of aux power"
Unit_Diag_Bit_Help(65) = "Check polarity."
Unit_Diag_Bit(66) = "Maximum line length exceeded"
Unit_Diag_Bit_Help(66) = "Check line length."
Unit_Diag_Bit(67) = "Corrosion/abrasion by medium"
Unit_Diag_Bit_Help(67) = "Replacement is recommended."
Unit_Diag_Bit(68) = "Fouling on sensor element"
Unit_Diag_Bit_Help(68) = "Cleaning is recommended."
Unit_Diag_Bit(69) = "Auxil medium missing or insuffic"
Unit_Diag_Bit_Help(69) = "Check auxiliary medium."
Unit_Diag_Bit(70) = "Wear reserve used up (operation)"
Unit_Diag_Bit_Help(70) = "Plan maintenance."
Unit_Diag_Bit(71) = "Wear reserve used up (wear)"
Unit_Diag_Bit_Help(71) = "Plan maintenance."
Unit_Diag_Bit(72) = "Error in peripherals"
Unit_Diag_Bit_Help(72) = "Check peripherals."
Unit_Diag_Bit(73) = "Electromag interference too high"
Unit_Diag_Bit_Help(73) = "Lower external electromagnetic interference."
Unit_Diag_Bit(74) = "Temperature of medium too high"
Unit_Diag_Bit_Help(74) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(75) = "Ambient temperature too high"
Unit_Diag_Bit_Help(75) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(76) = "Vibration/Impact load too high"
Unit_Diag_Bit_Help(76) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(77) = "Auxiliary power range off-spec"
Unit_Diag_Bit_Help(77) = "Check power supply"
Unit_Diag_Bit(78) = "Auxiliary medium missing"
Unit_Diag_Bit_Help(78) = "Check auxiliary medium."
Unit_Diag_Bit(79) = "Excessive temperature shock"
Unit_Diag_Bit_Help(79) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(80) = "Deviation from measurement"
Unit_Diag_Bit_Help(80) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(81) = "Humidity in electronics area"
Unit_Diag_Bit_Help(81) = "Replacement is recommended."
Unit_Diag_Bit(82) = "Medium in electronics area"
Unit_Diag_Bit_Help(82) = "Replacement is recommended."
Unit_Diag_Bit(83) = "Mechanical damage"
Unit_Diag_Bit_Help(83) = "Replacement is recommended."
Unit_Diag_Bit(84) = "Communication error"
Unit_Diag_Bit_Help(84) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(85) = "Foreign material in electro area"
Unit_Diag_Bit_Help(85) = "Replacement is recommended."
;NE107_ULTRASONIC(device specific)
Unit_Diag_Bit(104) = "Particle inclusions"
Unit_Diag_Bit_Help(104) = "Check process."
Unit_Diag_Bit(105) = "Gas bubbles in the liquid"
Unit_Diag_Bit_Help(105) = "Check process. Reduce gas bubbles in liquid."
Unit_Diag_Bit(106) = "Body fouling"
Unit_Diag_Bit_Help(106) = "Check body."
Unit_Diag_Bit(107) = "External ultrasonic waves"
Unit_Diag_Bit_Help(107) = "Eliminate external ultrasonic waves."
Unit_Diag_Bit(108) = "Sensor fouling"
Unit_Diag_Bit_Help(108) = "Clean sensor."
Unit_Diag_Bit(109) = "Erosion"
Unit_Diag_Bit_Help(109) = "Change sensor."
Unit_Diag_Bit(110) = "Faulty mounting (clamp on)"
Unit_Diag_Bit_Help(110) = "Check installation."
Unit_Diag_Bit(111) = "Pulsating flow"
Unit_Diag_Bit_Help(111) = "Check process."
Unit_Diag_Bit(112) = "Sound conductivity"
Unit_Diag_Bit_Help(112) = "Check configuration."
Unit_Diag_Bit(113) = "Signal lost due to overrange"
Unit_Diag_Bit_Help(113) = "Check configuration."
Unit_Diag_Bit(114) = "Flow profile disturbance"
Unit_Diag_Bit_Help(114) = "Check process."
Unit_Diag_Bit(115) = "Incomplete filling"
Unit_Diag_Bit_Help(115) = "Check process."
;---------------
UnitDiagType=254
X_Unit_Diag_Bit(35) = "Restart" ;DIA_WARMSTART
X_Unit_Diag_Bit(36) = "Application reset" ;DIA_COLDSTART
X_Unit_Diag_Bit(37) = "Maintenance required" ;DIA_MAINTENANCE
X_Unit_Diag_Bit(40) = "Maintenance alarm" ;DIA_MAINTENANCE_ALARM
X_Unit_Diag_Bit(41) = "Maintenance demanded" ;DIA_MAINTENANCE_DEMANDED
X_Unit_Diag_Bit(42) = "Function check" ;DIA_FUNCTION_CHECK
X_Unit_Diag_Bit(43) = "Out of specification" ;DIA_OUT_OF_SPEC
X_Unit_Diag_Bit(44) = "Parameter update" ;DIA_UPDATE_EVENT
X_Unit_Diag_Bit(55) = "Extension available"
;--- NE107_COMMON
X_Unit_Diag_Bit(56) = "Sensor element exciter faulty"
X_Unit_Diag_Bit_Help(56) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(57) = "Error in evaluation electronics"
X_Unit_Diag_Bit_Help(57) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(58) = "Error in internal energy supply"
X_Unit_Diag_Bit_Help(58) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(59) = "Error in sensor element"
X_Unit_Diag_Bit_Help(59) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(60) = "Error in actuator element"
X_Unit_Diag_Bit_Help(60) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(61) = "Faulty installat e.g. dead space"
X_Unit_Diag_Bit_Help(61) = "Check installation."
X_Unit_Diag_Bit(62) = "Parameter setting error"
X_Unit_Diag_Bit_Help(62) = "Check parameter settings for consistency."
X_Unit_Diag_Bit(63) = "Signal path broken or short cut"
X_Unit_Diag_Bit_Help(63) = "Check signal path."
X_Unit_Diag_Bit(64) = "Overloading"
X_Unit_Diag_Bit_Help(64) = "Check load."
X_Unit_Diag_Bit(65) = "Wrong polarity of aux power"
X_Unit_Diag_Bit_Help(65) = "Check polarity."
X_Unit_Diag_Bit(66) = "Maximum line length exceeded"
X_Unit_Diag_Bit_Help(66) = "Check line length."
X_Unit_Diag_Bit(67) = "Corrosion/abrasion by medium"
X_Unit_Diag_Bit_Help(67) = "Replacement is recommended."
X_Unit_Diag_Bit(68) = "Fouling on sensor element"
X_Unit_Diag_Bit_Help(68) = "Cleaning is recommended."
X_Unit_Diag_Bit(69) = "Auxil medium missing or insuffic"
X_Unit_Diag_Bit_Help(69) = "Check auxiliary medium."
X_Unit_Diag_Bit(70) = "Wear reserve used up (operation)"
X_Unit_Diag_Bit_Help(70) = "Plan maintenance."
X_Unit_Diag_Bit(71) = "Wear reserve used up (wear)"
X_Unit_Diag_Bit_Help(71) = "Plan maintenance."
X_Unit_Diag_Bit(72) = "Error in peripherals"
X_Unit_Diag_Bit_Help(72) = "Check peripherals."
X_Unit_Diag_Bit(73) = "Electromag interference too high"
X_Unit_Diag_Bit_Help(73) = "Lower external electromagnetic interference."
X_Unit_Diag_Bit(74) = "Temperature of medium too high"
X_Unit_Diag_Bit_Help(74) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(75) = "Ambient temperature too high"
X_Unit_Diag_Bit_Help(75) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(76) = "Vibration/Impact load too high"
X_Unit_Diag_Bit_Help(76) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(77) = "Auxiliary power range off-spec"
X_Unit_Diag_Bit_Help(77) = "Check power supply"
X_Unit_Diag_Bit(78) = "Auxiliary medium missing"
X_Unit_Diag_Bit_Help(78) = "Check auxiliary medium."
X_Unit_Diag_Bit(79) = "Excessive temperature shock"
X_Unit_Diag_Bit_Help(79) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(80) = "Deviation from measurement"
X_Unit_Diag_Bit_Help(80) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(81) = "Humidity in electronics area"
X_Unit_Diag_Bit_Help(81) = "Replacement is recommended."
X_Unit_Diag_Bit(82) = "Medium in electronics area"
X_Unit_Diag_Bit_Help(82) = "Replacement is recommended."
X_Unit_Diag_Bit(83) = "Mechanical damage"
X_Unit_Diag_Bit_Help(83) = "Replacement is recommended."
X_Unit_Diag_Bit(84) = "Communication error"
X_Unit_Diag_Bit_Help(84) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(85) = "Foreign material in electro area"
X_Unit_Diag_Bit_Help(85) = "Replacement is recommended."
;NE107_ULTRASONIC(device specific)
X_Unit_Diag_Bit(104) = "Particle inclusions"
X_Unit_Diag_Bit_Help(104) = "Check process."
X_Unit_Diag_Bit(105) = "Gas bubbles in the liquid"
X_Unit_Diag_Bit_Help(105) = "Check process. Reduce gas bubbles in liquid."
X_Unit_Diag_Bit(106) = "Body fouling"
X_Unit_Diag_Bit_Help(106) = "Check body."
X_Unit_Diag_Bit(107) = "External ultrasonic waves"
X_Unit_Diag_Bit_Help(107) = "Eliminate external ultrasonic waves."
X_Unit_Diag_Bit(108) = "Sensor fouling"
X_Unit_Diag_Bit_Help(108) = "Clean sensor."
X_Unit_Diag_Bit(109) = "Erosion"
X_Unit_Diag_Bit_Help(109) = "Change sensor."
X_Unit_Diag_Bit(110) = "Faulty mounting (clamp on)"
X_Unit_Diag_Bit_Help(110) = "Check installation."
X_Unit_Diag_Bit(111) = "Pulsating flow"
X_Unit_Diag_Bit_Help(111) = "Check process."
X_Unit_Diag_Bit(112) = "Sound conductivity"
X_Unit_Diag_Bit_Help(112) = "Check configuration."
X_Unit_Diag_Bit(113) = "Signal lost due to overrange"
X_Unit_Diag_Bit_Help(113) = "Check configuration."
X_Unit_Diag_Bit(114) = "Flow profile disturbance"
X_Unit_Diag_Bit_Help(114) = "Check process."
X_Unit_Diag_Bit(115) = "Incomplete filling"
X_Unit_Diag_Bit_Help(115) = "Check process."
EndUnitDiagType
;-------------------------------------------------------------------------
;
;max module text length-----------------"
Module="Not in cyclic data transfer " 0x00 ;Empty module
0
Info_Text="No cyclic data selected for this slot. Function disabled"
EndModule
Module="Volume flow" 0x42,0x84,0x08,0x05
1
EndModule
Module="Sound velocity" 0x42,0x84,0x08,0x05
2
EndModule
Module="Volume" 0x41,0x84,0x85
3
Ext_Module_Prm_Data_Len = 7
Ext_User_Prm_Data_Const(0) = 7,67,3,0,0x04,0x0A,1
Ext_User_Prm_Data_Ref(4) = 4 ;units (Unsigned16)
;INPUT_SELECTOR fixed to 1 (= volume flow)
EndModule
Module="Volume, Set" 0xC1,0x80,0x84,0x85
4
Ext_Module_Prm_Data_Len = 7
Ext_User_Prm_Data_Const(0) = 7,67,3,0,0x04,0x0A,1
Ext_User_Prm_Data_Ref(4) = 4 ;units (Unsigned16)
;INPUT_SELECTOR fixed to 1 (= volume flow)
EndModule
;----------- Description of the module assignment: ---------------------
;
SlotDefinition
Slot(1) = "" 1 1 ;always plugged
Slot(2) = "" 2 0,2
Slot(3) = "" 3 0,3,4
EndSlotDefinition